Service operation at Matanzas power plant (Cuba)
Last December we managed to find a rapid solution for our client Energoimport and the end user UNE: we restored the operation of Matanzas’ “A. Guiteras” power plant after a failure in the auxiliary services transformer, which damaged the main connection bus duct between the generator and power transformer.
The Main duct, air insulated, is realized in octagonal aluminium profile 99.5%.
Rated Current 9750 A.
Short-circuit current 107 kA.
Insulating Voltage 24 kV.
Design, construction of the busbar duct and shipment by air in less than a month. The power plant has been successfully put back in service in a very short time.